import org.lsst.ccs.description.groovy.CCSBuilder
import org.lsst.ccs.bootstrap.BootstrapResourceUtils
import org.lsst.ccs.subsystem.refrig.RefrigMain
import org.lsst.ccs.subsystem.refrig.ColdCompressor
import org.lsst.ccs.subsystem.refrig.ColdCompLimits
import org.lsst.ccs.subsystem.refrig.FanControl
import org.lsst.ccs.subsystem.refrig.CompMaq20Device
import org.lsst.ccs.subsystem.refrig.CompMaq20DiscControl
import org.lsst.ccs.subsystem.refrig.CompMaq20PWMControl
import org.lsst.ccs.subsystem.refrig.CompPlutoDevice
import org.lsst.ccs.subsystem.refrig.A1000Device
import org.lsst.ccs.subsystem.refrig.SimCompPlutoDevice
import org.lsst.ccs.subsystem.refrig.SimA1000Device
import org.lsst.ccs.subsystem.common.devices.dataforth.Maq20PulseControl
import org.lsst.ccs.subsystem.common.devices.dataforth.Maq20AnalogControl
import org.lsst.ccs.subsystem.refrig.SubCoolingChannel
import org.lsst.ccs.monitor.Channel

Properties props = BootstrapResourceUtils.getBootstrapSystemProperties()

runMode = props.getProperty("org.lsst.ccs.run.mode", "normal")
if (runMode.equals("simulation")) {
    compPlutoDevice = SimCompPlutoDevice
    a1000Device = SimA1000Device
}
else {
    compPlutoDevice = CompPlutoDevice
    a1000Device = A1000Device
} 
compMaq20Device = CompMaq20Device
compMaq20PWMControl = CompMaq20PWMControl
maq20DiscControl = CompMaq20DiscControl
maq20PulseControl = Maq20PulseControl
maq20AnalogControl = Maq20AnalogControl

CCSBuilder builder = ["refrig-coldtest"]

builder.main (RefrigMain) {

    coldCompLimits (ColdCompLimits)

    comp = "Cold1"
    "$comp" (ColdCompressor, discTempChan: "DischrgTmp_P", discPressChan: "DischrgPrs",
             suctTempChan: "SuctionTmp_P", cmprPowerChan: "CompPower", liquidTempChan: "LiquidTmp_P") {

        FanCtrl (FanControl, fanCntrl: ["$comp/Maq20/FanControl"],
                 ambientTemp: "$comp/AmbientTmp", cabinetTemp: "$comp/CabinetTmp")

        Plc (compPlutoDevice)

        Maq20 (compMaq20Device, modules: ["TTC", "DIOL:pwm:pulse", "DIOL:pulse:pulse", "VO"]) {

            FanControl (compMaq20PWMControl, modIndex: 1, funcIndex: 0, frequency: 200.0)

            PulseControl0 (maq20PulseControl, modIndex: 1, funcIndex: 1, pulsesPerRevn: 6)

            PulseControl1 (maq20PulseControl, modIndex: 2, funcIndex: 0, pulsesPerRevn: 6)

            PulseControl2 (maq20PulseControl, modIndex: 2, funcIndex: 1, pulsesPerRevn: 6)

            ValveControl (maq20AnalogControl, modIndex: 3, ranges: ["VP10", "VP10", "VP10"] as String[])

            LineControl  (maq20DiscControl, modIndex: 2)

        }

        Vfd (a1000Device)

        plc = "$comp/Plc"
        maq20 = "$comp/Maq20"
        vfd = "$comp/Vfd"

        DischrgTmp_P (Channel, description: "Discharge Temperature (PLC)", units: "\u00b0C", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:0", scale: 0.01)

        DischrgTmp_M (Channel, description: "Discharge Temperature (Maq20)", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 3, type: "0", subtype: "T220")

        DischrgPrs   (Channel, description: "Discharge Pressure", units: "psia", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:3", scale: 0.1)

        SuctionTmp_P (Channel, description: "Suction Temperature (PLC)", units: "\u00b0C", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:1", scale: 0.01)

        SuctionPrs   (Channel, description: "Suction Pressure", units: "psia", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:4", scale: 0.1)

        LiquidTmp_P  (Channel, description: "Liquid Temperature (PLC)", units: "\u00b0C", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:2", scale: 0.01)

        LiquidTmp_M  (Channel, description: "Liquid Temperature (Maq20)", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 1, type: "0", subtype: "T220")

        PriOilSepTmp (Channel, description: "Primary Oil Separator Temp", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 2, type: "0", subtype: "T220")

        SecOilSepTmp (Channel, description: "Secondary Oil Separator Temp", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 7, type: "0", subtype: "T220")

        CompVoltage  (Channel, description: "Compressor Voltage", units: "Volts", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:6", scale: 0.1)

        CompCurrent  (Channel, description: "Compressor Current", units: "Amps", format: ".1f",
                      devcName: plc, hwChan: 1, type: "ADDREG:5", scale: 0.01)

        CompPower    (Channel, description: "Compressor Power", units: "VA", format: ".1f",
                      devcName: plc, hwChan: 0, type: "ADDINT:9", scale: 0.001)

        CompVfdVolt  (Channel, description: "Compressor VFD Voltage", units: "Volts", format: ".1f",
                      devcName: vfd, hwChan: A1000Device.CHAN_VOLTAGE)

        CompVfdCurr  (Channel, description: "Compressor VFD Current", units: "Amps", format: ".1f",
                      devcName: vfd, hwChan: A1000Device.CHAN_CURRENT)

        CompVfdFreq  (Channel, description: "Compressor VFD Frequency", units: "Hz", format: ".1f",
                      devcName: vfd, hwChan: A1000Device.CHAN_FREQUENCY)

        CompVfdTemp  (Channel, description: "Compressor VFD Temperature", units: "\u00b0C", format: ".0f",
                      devcName: vfd, hwChan: A1000Device.CHAN_TEMPERATURE)

        HGBValvePosn (Channel, description: "HGB Valve Position", units: "%", format: ".1f",
                      devcName: maq20, hwChan: CompMaq20Device.CHAN_HGB_VALVE, type: "3", scale: 10.0)

        EEPRValvePosn (Channel, description: "EEPR Valve Position", units: "%", format: ".1f",
                       devcName: maq20, hwChan: CompMaq20Device.CHAN_EEPR_VALVE, type: "3", scale: 10.0)

        WaterInTmp   (Channel, description: "Water Inlet Temperature", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 0, type: "0", subtype: "T220")

        WaterOutTmp  (Channel, description: "Water Outlet Temperature", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 4, type: "0", subtype: "T220")

        CabinetTmp   (Channel, description: "Cabinet Temperature", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 6, type: "0", subtype: "T220")

        AmbientTmp   (Channel, description: "Ambient Temperature", units: "\u00b0C", format: ".1f",
                      devcName: maq20, hwChan: 5, type: "0", subtype: "T220")

        Fan1Speed    (Channel, description: "Fan 1 Speed", units: "rpm", format: ".0f",
                      devcName: maq20, hwChan: CompMaq20Device.CHAN_PULSE_RPM, type: "1", subtype: "1")

        Fan2Speed    (Channel, description: "Fan 2 Speed", units: "rpm", format: ".0f",
                      devcName: maq20, hwChan: CompMaq20Device.CHAN_PULSE_RPM, type: "2", subtype: "0")

        Fan3Speed    (Channel, description: "Fan 3 Speed", units: "rpm", format: ".0f",
                      devcName: maq20, hwChan: CompMaq20Device.CHAN_PULSE_RPM, type: "2", subtype: "1")

        LiquidSubCooling   (SubCoolingChannel, description: "$comp SubCooling", units: "\u00b0C", format: ".2f",
                    dischargePressureChannel: ref("$comp/DischrgPrs"), liquidTempChannel:ref("$comp/LiquidTmp_M"))
    }

}
