import org.lsst.ccs.description.groovy.CCSBuilder;
import org.lsst.ccs.subsystem.refrig.Subscale;
import org.lsst.ccs.subsystem.refrig.TempControl;
import org.lsst.ccs.subsystem.refrig.MCCDevice;
import org.lsst.ccs.subsystem.refrig.BK1696Device;
import org.lsst.ccs.subsystem.refrig.WUDevice;
import org.lsst.ccs.monitor.Alarm;
import org.lsst.ccs.monitor.Line;
import org.lsst.ccs.monitor.Channel;

String limitLo = "limitLo"
String limitHi = "limitHi"

CCSBuilder builder = ["ccs-refrig-hxtest"]

builder.main (Subscale, argMap("main", 10000, 1000, 5000, 
                               ["CmprLine1", "CmprLine2"],
                               ["LoadLine1", "LoadLine2"],
                               null, ["LoadTemp"], ["LoadTemp"], null)) {

    TempCtrl   (TempControl, argMap(10, 1000, 120, 100, 4, 0, 0.05, 30000))

    Cmpr       (MCCDevice, argMap("TC_AI", "00099271"))

    Mod1       (MCCDevice, argMap("TC_AI", "00099629"))

    Mod2       (MCCDevice, argMap("TEMP", "0197DA2B"))

    Mod3       (MCCDevice, argMap("TEMP", "01923E75"))

//    Power      (BK1696Device, argMap("FTDI", ""))

    WattsLoad  (WUDevice, argMap(null, "AD01ZYPR"))

    CmprLine1  (Line, argMap("Cmpr", 0, null, 0))

    CmprLine2  (Line, argMap("Cmpr", 1, null, 0))

    LoadLine1  (Line, argMap("Mod1", 0, null, 0))

    LoadLine2  (Line, argMap("Mod1", 1, null, 0))

    AlarmCmpr  (Alarm, argMap("Trips off all power", null, 0))

    AlarmLoad  (Alarm, argMap("Turns off load power", null, 1))

    CmprPower  (Channel,
                argMap("Compressor\\Power", "Watts",
                       "Cmpr", 6, "VOLTS", "10V", 0.0, 208.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    CmpDisPrs  (Channel,
                argMap("Discharge pressure", "Psig",
                       "Cmpr", 5, "VOLTS", "1.25V", 0.0, 10000.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    CmpSucPrs  (Channel,
                argMap("Suction pressure", "Psig",
                       "Cmpr", 4, "VOLTS", "1.25V", 0.0, 1000.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    CmpBodyTmp (Channel,
                argMap("Body temperature", "\u00b0C",
                       "Cmpr", 0, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    CmpDisTmp  (Channel,
                argMap("Discharge temperature", "\u00b0C",
                       "Cmpr", 1, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    CmpRetnTmp (Channel,
                argMap("C1 oil temperature", "\u00b0C",
                       "Cmpr", 2, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    CmpSepTmp  (Channel,
                argMap("Separator temperature", "\u00b0C",
                       "Cmpr", 3, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    CmpFlowSwi (Channel,
                argMap("Flow switch state", ".0f", "",
                       "Cmpr", 6, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    CmpTmpRly  (Channel,
                argMap("Temperature relay state", ".0f", "",
                       "Cmpr", 4, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    C3LiqdTmp  (Channel,
                argMap("Heat Exchanger\\C3 liq capillary temperature", "\u00b0C",
                       "Mod1", 1, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    PreC4Tmp   (Channel,
                argMap("Pre C4 temperature", "\u00b0C",
                       "Mod1", 2, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    PostC4Tmp  (Channel,
                argMap("Post C4 temperature", "\u00b0C",
                       "Mod1", 3, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    HexVapPrs  (Channel,
                argMap("Vapor supply pressure", "Psig",
                       "Mod1", 4, "VOLTS", "1.25V", -2.5, 10000.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    HexLiqPrs  (Channel,
                argMap("Liquid supply pressure", "Psig",
                       "Mod1", 5, "VOLTS", "1.25V", -5.48, 5000.0,
                       "flag", 0.0, 0.0, null,
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    HexPrsDiff (Channel,
                argMap("Vapor/liquid delta P", "Psi",
                       null, 0, "DIFF", "HexLiqPrs:HexVapPrs", 0, 0,
                       "none", 0.0, 0.0, null,
                       "none", 0.0, 0.0, null))

    HexSucPrs  (Channel,
                argMap("Return pressure", "Psig",
                       "Mod1", 6, "VOLTS", "1.25V", 0.38, 1000.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    HexExitTmp (Channel,
                argMap("Return temperature", "\u00b0C",
                       "Mod2", 2, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    LoadTemp   (Channel,
                argMap("Load temperature RTD", "\u00b0C",
                       "Mod3", 0, "TEMP", "RTD:3WIRE", 0.0, 1.0,
                       "alarm", 0.0, 0.0, "AlarmCmpr",
                       "alarm", 0.0, 0.0, "AlarmCmpr"))

    LoadPower  (Channel,
                argMap("Heat load power", "Watts",
                       "WattsLoad", 0, "POWER", "", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    AmbientTmp (Channel,
                argMap("Ambient temperature", "\u00b0C",
                       "Mod1", 0, "TEMP", "TC:T", 0.0, 1.0,
                       "flag", 0.0, 0.0, null,
                       "flag", 0.0, 0.0, null))

    Running    (Channel,
                argMap("Control Chassis\\Running state", ".0f", "",
                       "Mod1", 6, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    Interlock  (Channel,
                argMap("Interlock state", ".0f", "",
                       "Mod1", 2, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    ThermRelay (Channel,
                argMap("Thermal relay state", ".0f", "",
                       "Mod1", 3, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    LoadEnable (Channel,
                argMap("Load enable state", ".0f", "",
                       "Mod1", 4, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))

    V5Power    (Channel,
                argMap("5-Volt power state", ".0f", "",
                       "Mod1", 5, "SWITCH", "", 0, 1,
                       "flag", 1.0, 0, null,
                       "flag", 1.0, 0, null))
}
